# Hanging a dipole from a tree not code compliant?

I just got off the phone with my town's electrical inspector (in Massachusetts), and he informed me that you are not allowed to hang anything electrical from "vegetation". He said if I did this with my dipole, that it would not pass inspection. He said that he can get me the NEC reference for this by sometime next week.

Has anyone dealt with this before? This is hard to believe considering so many people have dipoles. Are trees only technically ok for temporary installations?

The reason that I was talking to the inspector was because I was asking about oddities related to my electrical system + grounding. Then he blew up my world with the tree thing!

Update: This is the only relevant code reference that I have found on my own:

225.26 Vegetation as Support Vegetation such as trees shall not be used for support of overhead conductor spans.

You are apparently allowed to support lighting fixtures on trees per:

410.36(G) states that trees may be used to support fixtures. > This section contains two FPNs. The FPNs refer you to 225.6, which has the requirement overhead conductors may not be supported by trees. This includes the final means of attachment. In other words: A fixture mounted on a tree cannot be fed with overhead conductors.

My interpretation of this is you shouldn't have wire hung in the air feeding a tree. Versus running a wire up a tree. If you take 225.26 on it's own, you could maybe argue that vertically hanging an antenna is no good? Maybe I don't understand the definition of overhead conductor?

Update: 1/14/22 I talked to the electrical inspector again after giving him some NEC references (pasted below). He agrees that hanging an antenna from a tree is allowed. Woohoo! Thanks to everyone who commented (special thanks to @hobbs - KC2G). Hope this helps others in the future who may encounter the same issue with their town.

NEC references:

• 225.26 Vegetation as Support (vegetation not allowed)
• 230.10 Vegetation as Support (vegetation not allowed)
• 590.4(J) Support (vegetation not allowed)
• 810.12 Supports (no references to vegetation in this one)

Reading the following scope sections helps put these into context:

• 225.1 Scope
• 230.1 Scope
• 590.1 Scope
• 810.1 Scope

The absence of any wording related to vegetation or trees in 810.12 Supports is what seals the deal that hanging an antenna from a tree is allowed. If it was forbidden, it would really need to be noted here just like in the other sections about support which are tailored power supplying conductors.

• He's prob referring to the prohibition of using trees/vegetation for support of electric service. I would expect his purview to end at the outlet; in the same way he doesn't inspect the innards of your WiFi router appliance just because it's plugged into the mains, I would expect the transmission line & antenna hanging off your radio appliance are beyond his purview. Jan 13 at 15:56
• So that means you can't run speaker wire through your tree either? How about Christmas lights? Jan 13 at 16:32
• Yes, the NEC applies, but it is in Article 810 that your inspector is likely not familiar with. Generally the NEC is not available on the web, but ecmweb.com/national-electrical-code/code-basics/article/… has some info. Jan 13 at 17:16
• @kr4sh - correct - 810 applies to antennas, so if it doesn't say anything about it there is no prohibition. Each section has a 'Scope' associated with it, and they are misapplying one article into another article's scope. Jan 13 at 17:42
• The antenna is not a "conductor" that "transmits" power from point A to point B, it's a radiator. And no, you shouldn't hang your antenna from a tree, it might catch the tree on fire. You should hang your insulator from the tree, and hang the antenna from the insulator. Jan 14 at 5:12